|Type:||Residual Current, Electronic,electromagnetic||Poles Number:||2P|
|Rated Frequency:||50/60Hz||Rated Voltage:||240V/415V|
|Rated Current:||63A||Leakage Action Current:||30mA,100mA,300mA|
|Breaking Capability:||6KA/10KA||Application:||Short-circuit Protection,Electrical Power,earth Leakage Protection|
|Material:||Copper,High Standard Plastic Silver Copper,Silver Contact,Flame Resistant Plastic||Endurance:||4000|
|Printing:||Standard Or Customized||Protection Degree:||IP 20|
residual current operated circuit breaker,
differential switch circuit breaker
NBSe BFL62 Series Residual Current Circuit Breaker 2P 63A,rcd mcb
BFL62 residual current circuit breaker is suitable to the circuit of AC50/60Hz.rated voltage 230V for 2 poles and 400V for 4 poles, and rated current up to 63A.when people come across the electric shock or the leakage current of the electrical network exceeds the fixed value, this product can cut off the fault current in short period so as to protect person and the equipments, It also can be used in the infrequent starting of the circuit and motors.
The circuit breaker is suitable to industry, commerce, high-rise building, household and other kinds of places.
This product meets the standard of IEC/EN61008-1.
It has the following features:
In complicance with IEC/EN61008-1
Bilateral busbar wiring capabilities to adapt to the wider use of premises.
With functions of fault indicator.
Maximum connecting ability of 25mm2,wiring torque 3N *m, applicable to a variety of installing equipments,
2. Technical Data
|Product Name||Residual Current Circuit Breaker RCCB|
|Rated Current In||16A 25A 40A 63A|
|Poles||2P 4P 1P+N 3P+N|
|Rated Voltage Ue||2P: 230V 4P: 400V|
|Rated Sensitivity||10mA 30mA 100mA 300mA 500mA|
|Rated residual making and breaking capacity||500(In=25-40A) 630(In=63A)|
|Certificate||CE CB RohS WEEE CCC|
3. OPERATION PRINCIPLE FIG.
4. WORKING PRINCIPLE
RCCB (Residual Current Circuit Breaker)
There are two types of electrical faults which are very dangerous. One is when there is a high current fault due to some short circuit current, which can be protected by an MCB. Second is when earth leakage arises due to wet hands touched by someone. And an MCB cannot detect this fault, whereas it can be detected by the RCCB. The main principle behind the function of the RCCB is when current is flowing through the appliances it may return in full. There is the difference of milliampere and it may detect and trip the power supply in the circuit. When the current flows out from the appliances, then it is known as residual current. The RCCB is designed in such a way so that the difference can be compared between residual current values between the live and the neutral wires. If there is a small change between the current value of an account, it will trigger the RCCB to trip the circuit. Now it can be said that RCCBs sense the difference between the current value in phase and neutral and can break the circuit.
In the RCCB circuit breaker, the ON and OFF buttons are clearly visible with the help of a window provided at the top of the housing. With the use of advanced technology, some of the manufacturers have come out with the entire protection for the short circuit as well as for the earth fault, this device is also known as the RCBO. In such a situation, the MCB is not required.
Q1: What's your product Range?
- Shell Unti-fire. nylon pa66 or not unti-fire.
- Parts, Copper or iron
- Point Sliver point or Copper point
Q2: Are you a manufacturer?
A. Yes, we are only produce the circuit breaker over 20 years from 1999.
Q3: Do you have stock products to sell?
A. No,we work on OEM orders, The means, material, quantity,packing solution,etc will depend on your requests.obviously, your logo can be printed on the products.
Q4. what's the payment term?
A. We accept TT,30% deposit and 70% balance agaisnt copy of BL
Q5. how's the delivery time ?
A. usually it will take about 30 days for 30000pcs
Q6. tell me the standard of package?
A. Normally are cartons, color box or white box
Q7. what kind of material of circuit breaker?
A. we have two types, one copper coil with silver point and the other is brass coil with copper point. It depends on your requirement. In fact, those two have no difference if normal work well. Only except the electrical life. Copper and silver is better and also higer price.
Q8. We want to know month capacity.
Q9. Where is your market?
A. Our products are popular in Western Europe, Middle-East, Afirca, South Asia ,South Ameirca countries and area. Some of them are our regular customers and some of them are developing. We hope you can join us and make mutural benifit from our cooperation.
Q10. what kind of certificate you have ?
A. CE, CB,CCC,ISO9000.
Q11. Do you inspect the finished products
A. Yes.Each step of products will be inpected by QC department before shipping.
Q12. How are you ship the finished products?
- By Sea
- By plane
- By counties,TNT, DHL,FEDEX,UPS.etc.