|Type:||Residual Current, Electronic,electromagnetic||Rated Frequency:||50/60Hz|
|Rated Voltage:||240V/415V||Rated Current:||6A-63A|
|Leakage Action Current:||30mA,100mA,300mA||Standard:||IEC61008-1|
|Warranty:||2 YEARS||Breaking Capability:||6KA/10KA|
|Poles Number:||2,4,3,1P+N||Product Name:||Residual Current Circuit Breaker|
|Material:||Copper,High Standard Plastic Silver Copper,Silver Contact,Flame Resistant Plastic||Color:||White|
|Mechanical Life:||10000 Times||Endurance:||4000|
|Protection Degree:||IP 20||Rated Operating Voltage:||400V|
residual current device,
differential switch circuit breaker
NBSe NBSL1-100 Series Residual Current Circuit Breaker up to 100A,30mA RCD
NBSL1-100 series residual current circuit breakers are applied to the lines with AC 50/60Hz,rated voltage of230V(1P+N) or 400V(3P+N),and rated current of 63A.In case of electric shock or electric leakage current exceeds the specified value, the residual current circuit breaker can switch off the fault circuit in a very short time, protecting the safety of person and electric equipment.
Can be used in the industrial, commercial, high-rise buildings, civil residences and other places.
2. TECHNICAL PARAMETER
|Rated Operating voltage(Ue)||230V(1P+N)/400V(3P+N)|
|Characteristic||A type, AC type, S type|
|Rated Insulation voltage(Ui)||500V|
|Rated residual current (IΔn)||10,30,100,300mA|
|Rated residual switching on and||800A|
|Rated residual short-circuit current||6000A|
|Rated short-circuit current limit(Inc)||6000A|
|Rated switching on and breaking capaity(Im)||800A|
|Maximun breaking time(IΔm)||0.3s|
|Rated impulse withstand voltage(Uimp)||6kV|
|Mechanical life(times)||＞10,000 times|
|Comply with Standard||IEC 61008|
|Certificate||CE, CB, RoHS,WEEE|
|Humidity||40℃ humidity notexceed 50% 20℃ humidity not exceed 90%|
|(Condensation on the product due to|
|changes in humidity has been considered)|
|Working Temperature||-5℃~+40℃ and its average over aperiod of 24h does not exceed|
|Magnetic field||No more than 5 times the geomagnetic field|
|Mounting and Wiring|
|Shock and vibration||Should be installed in the case of no obvious impact vibration|
|Terminal connection types||type cable,type U bus, TH 35mm Din-rail|
|Wiring terminal connection conductor||1.5～25 mm²|
|Wiring terminal copper size||25 mm²|
|Installation mode||UsingTH35-7.5 profile installation, the title of|
|installation face and vertical face is not greater than5°|
|Wiring incoming mode||upper and lower incoming is possible for ELM type,|
|only upper incoming for ELE type|
3. OPERATION PRINCIPLE FIG.
RCCB (Residual Current Circuit Breaker)
There are two types of electrical faults which are very dangerous. One is when there is a high current fault due to some short circuit current, which can be protected by an MCB. Second is when earth leakage arises due to wet hands touched by someone. And an MCB cannot detect this fault, whereas it can be detected by the RCCB. The main principle behind the function of the RCCB is when current is flowing through the appliances it may return in full. There is the difference of milliampere and it may detect and trip the power supply in the circuit. When the current flows out from the appliances, then it is known as residual current. The RCCB is designed in such a way so that the difference can be compared between residual current values between the live and the neutral wires. If there is a small change between the current value of an account, it will trigger the RCCB to trip the circuit. Now it can be said that RCCBs sense the difference between the current value in phase and neutral and can break the circuit.
In the RCCB circuit breaker, the ON and OFF buttons are clearly visible with the help of a window provided at the top of the housing. With the use of advanced technology, some of the manufacturers have come out with the entire protection for the short circuit as well as for the earth fault, this device is also known as the RCBO. In such a situation, the MCB is not required.
Q1: What's your product Range?
- Shell Unti-fire. nylon pa66 or not unti-fire.
- Parts, Copper or iron
- Point Sliver point or Copper point
Q2: Are you a manufacturer?
A. Yes, we are only produce the circuit breaker over 20 years from 1999.
Q3: Do you have stock products to sell?
A. No,we work on OEM orders, The means, material, quantity,packing solution,etc will depend on your requests.obviously, your logo can be printed on the products.
Q4. what's the payment term?
A. We accept TT,30% deposit and 70% balance agaisnt copy of BL
Q5. how's the delivery time ?
A. usually it will take about 30 days for 30000pcs
Q6. tell me the standard of package?
A. Normally are cartons, color box or white box
Q7. what kind of material of circuit breaker?
A. we have two types, one copper coil with silver point and the other is brass coil with copper point. It depends on your requirement. In fact, those two have no difference if normal work well. Only except the electrical life. Copper and silver is better and also higer price.
Q8. We want to know month capacity.
Q9. Where is your market?
A. Our products are popular in Western Europe, Middle-East, Afirca, South Asia ,South Ameirca countries and area. Some of them are our regular customers and some of them are developing. We hope you can join us and make mutural benifit from our cooperation.
Q10. what kind of certificate you have ?
A. CE, CB,CCC,ISO9000.
Q11. Do you inspect the finished products
A. Yes.Each step of products will be inpected by QC department before shipping.
Q12. How are you ship the finished products?
- By Sea
- By plane
- By counties,TNT, DHL,FEDEX,UPS.etc.